1 Sep Damage to Steam Turbines Used for Electric Power Generation – Fossil Fueled Plants,” ASME TDP-1 TDP-1 was originally published. 25 May Buy ASME TDP Recommended Practices For Prevention Of Water Damage To Steam Turbines Used For Electric Power Generation. Generation – Fossil Fueled Plants,” ASME TDP-1 TDP-1 was originally published in and subsequently revised in , and The new.
|Published (Last):||17 January 2014|
|PDF File Size:||3.34 Mb|
|ePub File Size:||17.62 Mb|
|Price:||Free* [*Free Regsitration Required]|
Print asme tdp 1 2006 2 3 4 5 page sstarting from page current page. They were placed on your computer when you launched this website. If Vactual exceeds the sonic velocity Vs, then increase the value of P2 until Vactual is equal to Vs.
Sizing Water Heater Capacity. This Standard is not intended to impose new requirements retroactively for existing facilities. The sources treated herein specifically are those found to be most frequently involved in causing damage to turbines.
Drains installed downstream of attemperators are usually fitted with a drain pot with level instrumentation and are used asme tdp 1 2006 collect and remove spray water leakage downstream of the attemperating station. The solution process begins with an assumed value of Pc, and the asme tdp 1 2006 flow rate is calculated using the basic Bernoulli equation and the sonic velocity using equation .
Turbine water induction damages the same turbine internals due to warping, cracking, or distortion of metal parts caused by severe quenching of the hot casing, rotor shaft, and blades.
Preventing Turbine Water Damage: TDP-1 Updated
When discharging to the condenser, the manifold serves as a single connection to the condenser. In this case, the choke point rdp as pressure falls off and velocity increases to sonic velocity at the downstream end of the pipe. Please enter your email address. Asme tdp 1 2006 is included at the request of the publisher, as it helps them protect their copyright by restricting file sharing.
As,e were no books found for the applied search filters.
Proper Sizing of Steam Header Drains Prevents Water Induction ASME TDP-1 –
Copyright Compu-tecture, Inc. FORMAT Single User Subscription Site License Subscription BOOKS All Asme tdp 1 2006 PACKAGES All Packages EDITION to PUBLISHER. The pressures assumed in the figure are typical of the range of values experienced in steam headers during start-up of the STG.
They were placed on your computer when you launched this website. As expected, the mass flow rate decreases as the drain line resistance increases. Now use P2 and v 2 to establish the sonic velocity Vsaccording to equation : Figure 2 illustrates the percentage of times asme tdp 1 pdf events asme tdp 1 2006 to water Asme tdp 1 free download Asme tdp 1 pdf free download links.
Calculating blowdown flow rate. The modified Darcy formula can be represented as follows, in equation : Full Description This Standard includes recommended practices concerned primarily asme tdp 1 2006 the prevention of water damage to steam turbines used for fossil-fuel-fired electric power generation.
The results are expected to facilitate the txp of the plant designer asme tdp 1 2006 providing good estimates for two-phase discharge flow through the drain line. This mass flow rate was also evaluated for the same 2-inch drain used in a typical power plant Figure 5. What you can do with a Secure PDF: Founded in asem a small group of leading industrialists, ASME has grown through the decades to include more thanmembers in asme tdp 1 2006.
The downstream choked flow pressure asme tdp 1 2006 be determined using an iterative calculation methodology. Not Logged In Member?: The steam header drains can also be connected directly to asmw vent stack that is open to the atmosphere and fitted with a bottom drain for condensate removal. Remember me for one month. Note that for a given steam header pressure P1 the rate of steam flow through the pipe reaches steady-state conditions for long pipes.
Windows XPVista78 Total downloads: Full Description This Standard includes recommended practices concerned primarily with the prevention of water damage to steam turbines used for fossil-fuel-fired electric power generation. These drain valves can also be programmed to open or remain closed depending on location and function during an STG trip condition. When the two asme tdp 1 2006 are equal, this condition represents ttdp flow conditions at the vent outlet.
Zaheer Akhtar, PE Results from using this methodology were calculated for typical power plant steam header parameters illustrated in Figures 4 and 5. Asme tdp 1 2006 steam header drains are typically connected to a manifold that directs several drains from different locations to the condenser or the steam vent. ASME is a not-for-profit membership organization that enables collaboration, knowledge sharing, career enrichment, and skills development across all engineering disciplines, toward a goal of helping the global engineering community develop solutions to benefit lives and livelihoods.
The bottom of the vent stack is fitted with a drain line to discharge condensate collected at the bottom of the vent. To provide moisture-free steam to the STG, the supply steam lines need to be adequately sloped and fitted with appropriately located drain lines capable of discharging any and all collected condensate Figure 1.
Asme tdp 1 2006 this situation, the drain line discharges superheated asme tdp 1 2006 at full pressure through a vent to the atmosphere.
Register for a trial account. In case of an atmospheric vent, the asme tdp 1 2006 may be directly connected to the vent or to a manifold connected to the vent. Are you sure you want to empty the asme tdp 1 2006 About ASME ASME is a not-for-profit membership organization that enables collaboration, knowledge sharing, career enrichment, and skills development across all engineering amse, toward a goal of helping the global engineering community develop solutions to benefit lives and livelihoods.